Safe Handling of Medical Gas Cylinders
The use of medical gas cylinders in healthcare facilities is covered by the National Fire Protection Association (NFPA) standards (NFPA 99), the Occupational Safety and Health Administration (OSHA) standards (29 CFR 1910), and The Joint Commission Environment of Care Standard (EC.02.01.01 EP3). During facility surveys, The Joint Commission or OSHA can cite hospitals or surgery centers for improperly handling medical gas cylinders. The recommendations below will help you handle compressed medical gas cylinders safely and stay in compliance with the standards.
Segregate Full and Empty Cylinders
NFPA requires full and empty gas cylinders to be segregated when stored. Label stored gas cylinders by placing a “Full” or “Empty” sign on the storage cart, a tag around the neck of the cylinder, or signs on the wall space behind the stored cylinders. Labeling them is important to ensure that nurses can pick up a full oxygen cylinder when needed.
Secure All Cylinders
A compressed gas cylinder can become a flying missile if it falls on its stem and releases the high gas pressure. To avoid potential injury, property damage, or fire, never leave a cylinder standing free or unsecured on the top of a patient bed or cart. Medical gas cylinders should be secured in stands or carts or chained to walls. One chain is sufficient to secure the cylinders, except in seismic areas, where two chains are recommended.
Calculate the Maximum Oxygen Storage Limit
NFPA 99 limits the amount of oxygen stored in a smoke zone to 300 cubic feet. Each E-size cylinder holds 25 cubic feet of oxygen, so the maximum number of E cylinders allowed is 12. Keep in mind that a large H cylinder holds 250 cubic feet of oxygen, so the maximum number allowed to be stored in a smoke zone would be one H cylinder and two E cylinders.
- “In Use” Exception—Oxygen cylinders attached to an anesthesia machine, wheelchair, or patient cart are considered “in use” and are not counted when calculating the amount of oxygen stored in a smoke zone.
- Oxygen Storage Options—Some hospitals use special UL-rated fire cabinets to store more than 12 E cylinders in a smoke zone. For example, you could safely store 24 E cylinders or more in a cabinet with a one-hour rating. If you use a storage room with one-hour fire-rated walls and a 45-minute fire-rated door, you could store up to 3,000 cubic feet of oxygen. However, you would need to maintain a safe distance between the oxygen cylinders and any combustible materials in the room. If the storage room has sprinklers, only five feet of distance between the cylinders and combustible materials is required. If the room does not have sprinklers, a distance of 25 feet is required. The door to a large medical gas cylinder storage room should be kept locked.
Secure Outside Cylinder Storage
If stored outside, medical gas cylinders should be in a fenced area with a locked door or gate for security. NFPA 99 advises protecting cylinders during winter from accumulations of ice or snow and, during summer, screening cylinders from continuous exposure to direct rays of the sun in localities where extreme temperatures prevail. Consider installing a small roof over the medical gas cylinder storage area.